23.70.030 Local Amendment Regarding Electric Vehicle Charging For New One- and Two-Family Dwellings and Town-Houses
(a) Green Building Code Section 22.214.171.124, "New one- and two-family dwellings and town-houses with attached private garages," is amended to require the Tier 1 and Tier 2 requirement per Section A126.96.36.199 and A188.8.131.52.1 of the Green Building Code as follows:
(1) Tier 1 and Tier 2. For each dwelling unit, a dedicated 208/240-volt branch circuit shall be installed in the raceway required by Section 184.108.40.206. The branch circuit and associated overcurrent protective device shall be rated at 40 amperes minimum. Other electrical components, including a receptacle or blank cover, related to this section shall be installed in accordance with the California Electrical Code.
A220.127.116.11.1 Identification. The service panel or sub-panel circuit directory shall identify the overcurrent protective device designated for future EV charging purposes as "EV READY" in accordance with the California Electrical Code. The receptacle or blank cover shall be identified as "EV READY."